Boiler Manuals for the Worcester Greenstar 24I Junior NG appliance. View and Download Worcester GREENSTAR 24i junior instruction manual online . wall hung RSF gas-fired condensing combination boiler installation. View and Download Worcester GREENSTAR 24i junior instruction manual online . WALL HUNG RSF GAS FIRED CONDENSING COMBINATION BOILER.
|Published (Last):||27 July 2012|
|PDF File Size:||6.24 Mb|
|ePub File Size:||11.47 Mb|
|Price:||Free* [*Free Regsitration Required]|
Make connections to the heating system. Worcester 24i junior timer keeps losing time. Pull valve up and forward out of boiler. The addition of sealing agents to the system water is not recommended as this can cause problems with deposits left in the heat exchanger. These are not polarity sensitive. Wall mounted combination boilers for central heating and mains fed domestic hot water 65 pages.
Water Treatment The addition of sealing agents to the system water is not recommended as this can cause problems with deposits left in the heat exchanger. Re-assemble and refit boiler case. Isolate gas supply at boiler gas cock. Remove the support cable and fit to the new control.
You’ll need Adobe Reader to view it.
Jump to main content My Home My Business. Remove boiler bottom panel D and installer pack C. Worcester Greenstar 12i System Instruction Manual 74 pages.
Never terminate or discharge into any open source, including; sink, bath, shower, bidet, toilet etc. Page 15 Number, Date of Installation. Wall mounted combination boiler for central heating and mains kanual domestic hot water 36 pages. To print the manual completely, please, download it. Ensure any seals that have been disturbed are renewed. Expansion maunal The expansion vessel can be replaced with the boiler in position if there is a side exit flue fitted and there is a minimum clearance of mm above the boiler casing.
To refit, mmanual the above in reverse. Pre-commissioning Checks 3 Check that the condensate pipe has been connected to the syphon.
Got it, continue to print. The boiler will lie at an angle to the 2i to allow the boiler outer casing E to be removed. E upwards and slide the control support bracket F to the left.
Don’t show me this message again. If vertical flue is fitted then a similar clearance to one side and the flue is required.
Worcester 24i junior User Instructions & Customer Care Manual
Open all windows and doors. As you grefnstar already saved the maximum of 9 manuals to your online services account you need to delete one of these before you can save another one.
Book an engineer, pay bills, join Rewards and more Access your account.
Worcester cannot be held responsible 24l costs incurred by persons not deemed to be competent. Don’t have an account? This is to allow sufficient time for the setting procedure.
This manual also for: Removing outer case 1. Is the incoming gas pressure at least 18mbar with the boiler at maximum output?
Find the best energy tariff for you Get a quote. Plumbing Manifold Further guidance on pipe routing manuaal be found printed on the boiler template supplied with the boiler.
Catch the debris and condensate from the syphon into a suitable container. Gently raise the boiler off the mounting frame. This allows the heating system and mains water connec- tions to be filled and checked prior to boiler installation. Do not attempt to force beyond the limit stops.
Your account on the manuual Control your account from your phone or tablet.
Remove stainless steel viewing mirror F. Page 50 To refit, follow the above in reverse. F from the retaining bracket. When a demand is made for heating by the system controls i. Flue Installation C over the notches to secure.
Download your manuals
Carry on browsing if you’re happy with this, or click here to manage cookies. Electrics 5 Optional external frost stat connection ST6: Undo the flue connection from the sump and push the flue tube up. Pressure Relief Pipework as shown to help prevent freezing. UP until the stop on the inside of the handle is over the shoulder of the metal bracket to secure in place.
Page 51 To refit, follow the above in reverse. Remove seal from the top of the heat exchanger. Remove clamping plate K. Boiler Connections F from the junilr bracket.